Banaz TM – Çamsu DM ETL Electrical Installation;
8 settlements located between Banaz TM and Çamsu DM were fed by iron, wood and concrete pole line, which has already completed its economic life. Since the line is very old, continuous malfunctions occur and due to the absence of any breaker cabin on the line route, the fault in any place and all settlements were affected by this fault. For this reason, the Energy Transmission line between Banaz TM and Çamsu DM was renewed with galvanized bolted iron pole (124 units) and 21.8 km double circuit with 2x (3×3 / 0) conductors. A cutter measuring cabinet has been installed on the line route. For the 8 settlements on the route, a new Energy Transmission line with 13 poles, 1 km long 3xSW conductor, 12 poles 1.4 km long 3×1 / 0 conductor was installed.
Nuri Şeker Street LV + MV Electrical Installation
The facility of this area has been renewed due to the fact that the existing electrical installation in Nuri Şeker Street and its vicinity is very old and completed its economic life, continuous voltage drops occur, the 25 special transformer posts in this area are fed from only 2 transformer centers, and the MV malfunctions are intense and the whole region is affected during the breakdown. The electrical installation, which is the existing overhead line, has been established as an underground grid.
The MV lines of the new electrical installation were built according to the ring system, therefore, 2 Distribution Centers and 9 Monoblock transformer centers of various powers were established in the facility, and the number of subscribers to be affected in possible failures was minimized. In the facility, 483 galvanized lighting poles and 100.367 meters of underground cables in various types and sizes were used.
Village and neighborhood Electrical Installations;
Since the existing electrical installation of Uşak center 3 villages (Derdent, Çiğerdedeve and Eski Güney) and 3 villages of Banaz district (Kaylı, Hasanköy, Çöğurlu) are old, continuous malfunctions occur and there are constant voltage drops due to the fact that the existing lines cannot fully meet the energy needs, the electrical installation of the settlements have been renewed with concrete poles (830 units). In order to meet the energy needs of these 6 settlements, a total of 15 pole-type transformer posts of various powers have been installed. In addition, in case of malfunctions occurring in the ETLs connected to Uşak Central Selvioğlu village, Susuzören village and other villages in the vicinity of Öksüz village in Banaz District, 3 Cutter Measuring Cabins were installed in these villages to reduce the number of affected facilities, the number of breakdowns and the number of affected settlements were minimized.
Mixed OIZ Connection Work;
This facility was built in order to feed Bölme DM, Kalfa DM, Prison DM and Sivaslı group ETLs from the newly established TEİAŞ 100 MVA KOSB reducer center in Uşak center. For this work, 1 Distribution Center and an underground facility with 25197 mt MV cable of various types were built.
Kemal Öz Neighborhood LV + MV Electrical Installation;
Kemal Öz Neighborhood, located in the center of Uşak, is the new settlement area of the city and due to the dense construction, electrical installation of this neighborhood has been renovated by taking it underground since the existing overhead line LV + MV electrical installation has completed its economic life. Within the scope of this work, 2 prefabricated Distribution Centers, 12 Monoblock Concrete Transformer centers and 14 power transformers of various powers were used. In addition, 1436 galvanized lighting poles and 222,487 meters of LV + MV underground cables in various types and sizes were used in the facility.
Aybey DM – Hacıkadem DM LV + MV Electrical Installation;
Aybey District, located in the center of Uşak, is one of the densely settled areas of the city, and the current overhead line LV + MV electricity facility has completed its economic life and cannot meet the new construction. Because of the intensive power losses, the electricity facility of this neighborhood has been taken underground and renewed. Within the scope of this work, 6 Distribution Centers, 3 prefabricated and 3 MOD5B, 19 Monoblock Concrete Transformer centers, 26 power transformers of various powers were used. In addition, 926 galvanized lighting poles and 289,318 mt AG + OG underground cables in various types and sizes were used in the facility.